Bitcoin Forum
April 27, 2018, 09:41:07 AM
 News: Latest stable version of Bitcoin Core: 0.16.0  [Torrent]. (New!)
 Home Help Search Donate Login Register
 Pages: 1 [2]  All
 Author Topic: Power Configuration [BOUNTY 5BTC]  (Read 5495 times)
rjk
Sr. Member

Offline

Activity: 448
Merit: 250

1ngldh

 March 30, 2012, 07:38:00 PM

This might provide some insight on 208 vs 240: http://www.phaseconverterinfo.com/phaseconverter_deltawye.htm

Like I said, wye vs. Delta - they are different.

Mining Rig Extraordinaire - the Trenton BPX6806 18-slot PCIe backplane [PICS] Dead project is dead, all hail the coming of the mighty ASIC!
Advertised sites are not endorsed by the Bitcoin Forum. They may be unsafe, untrustworthy, or illegal in your jurisdiction. Advertise here.
1524822067
Hero Member

Offline

Posts: 1524822067

Ignore
 1524822067

1524822067
 Report to moderator
1524822067
Hero Member

Offline

Posts: 1524822067

Ignore
 1524822067

1524822067
 Report to moderator
Scared
Member

Offline

Activity: 70
Merit: 10

 March 30, 2012, 07:45:59 PM

So I didn't measure hot-hot.. Didn't think that was a wise idea at the time.. So after you mentioned it I decided I'd go measure it and found it's reading only 208V?!?!?! I double checked the Hot to Neutral and it's 120V. Show does 120V + 120V = 208V???

It should look like this:

W = neutral
X = one 115V leg
Y = one 115V leg
There is no ground on this outlet which is why it is obsolete.

X -> Y should be ~230V (220V-240V)
X -> W should be ~115V (110V-120V)
Y -> W should be ~115V (110V-120V)

I've tot a Leviton -

What I get when I measured the points you referenced -
X -> Y = Ranges between 208V and 210V
X -> W = 120V Solid
Y -> W = 120V Solid

Is it possible that it's wired incorrectly or am I just doing something incredibly stupid?

Scared
Member

Offline

Activity: 70
Merit: 10

 March 30, 2012, 07:59:16 PM

This might provide some insight on 208 vs 240: http://www.phaseconverterinfo.com/phaseconverter_deltawye.htm

Like I said, wye vs. Delta - they are different.

Ahha! I probably only understood 5% of article. Now you've got me wondering if my circuit is three-phase. From what I could understand about the article the only way to get 208V is from the difference between two phases in a three phase system. The difference between a phase and neutral would be 120V. That seems to be what I'm measure on my outlet. But why would anyone hookup a three phase socket  for office use?

silverbox
Legendary

Offline

Activity: 952
Merit: 1000

 March 30, 2012, 08:49:31 PM

The other legs of the 3 phase prob go to other offices.  You have 2 legs of 208 3 phase in that outlet.
Scared
Member

Offline

Activity: 70
Merit: 10

 March 30, 2012, 09:02:35 PM

The other legs of the 3 phase prob go to other offices.  You have 2 legs of 208 3 phase in that outlet.

Does that mean I treat it like a singe phase outlet then?
Inspector 2211
Sr. Member

Offline

Activity: 453
Merit: 250

 March 30, 2012, 09:18:59 PM

The other legs of the 3 phase prob go to other offices.  You have 2 legs of 208 3 phase in that outlet.

Does that mean I treat it like a singe phase outlet then?

Like TWO 110V single phase outlets.
Or like ONE 208V single phase outlet.

 ▄█▄            ▄█ ▀█▀     ▄ ▄███▄▄████▄▀ ▄▄▀▄    ▀█▄██████████▀▄█████▀▄▀   ▄█▀▄███████████████████▄ ▄██▀█▀▀▀▀███▀▀▀█████▄▄▄▀█▀▄ ▄█▀▀   ▀████▀▄████████ █▀█▄▄██▀  ▀ ▀ ▀██████████▄   ▄▀▀█▄     ▀ ▀  ███▀▀▀▀▀████▌ ▄  ▀          ████████████▌   █        █████████████▀        ▀▀▀██▀▀██▀▀           ▀▀  ▀▀ BTC-GREEN ▄▄█████████▄▄    ▄█████████████████▄  ▄█████████████████████▄ ▄███████████████████████▄▄█████████████████████████▄█████████████████████████████████████████████████████████████████████████████████▀█████████████████████████▀ ▀███████████████████████▀  ▀█████████████████████▀    ▀█████████████████▀       ▀▀█████████▀▀ Ecological Community in the Green Planet❱❱❱❱❱❱     WHITEPAGE   |   ANN THREAD     ❰❰❰❰❰❰ ▄███▄▄       ▄▄█████████▄      ▄█████████████▌   ▄████████████████▄▄ ▄███████████████████████████████████████████▄▄███████████████████████▀████████████████████████▀ ▀▀███████▀██▌████████▀   ▀██▀▀▀  ██  ▀▀▀▀▀▀           ██           ██▌          ▐███▄ .J O I N   I C O  IIILIVE
rjk
Sr. Member

Offline

Activity: 448
Merit: 250

1ngldh

 March 30, 2012, 09:25:09 PM

The other legs of the 3 phase prob go to other offices.  You have 2 legs of 208 3 phase in that outlet.

Does that mean I treat it like a singe phase outlet then?

Like TWO 110V single phase outlets.
Or like ONE 208V single phase outlet.
Yep. In any case, the electrician might be a good idea, since he will have to convert it to a 4-wire system. Right now you have 2 phases and a ground, but that is grandfathered in. Need 2 phases, a neutral, and a ground. At 208v, the rigs will pull a lot more amps than at 240v, but the only way to fix that would be to install a buck/boost transformer in boost mode. http://en.wikipedia.org/wiki/Buck%E2%80%93boost_transformer

Mining Rig Extraordinaire - the Trenton BPX6806 18-slot PCIe backplane [PICS] Dead project is dead, all hail the coming of the mighty ASIC!
DeathAndTaxes
Donator
Legendary

Offline

Activity: 1218
Merit: 1000

Gerald Davis

 March 30, 2012, 09:33:42 PM

Does that mean I treat it like a singe phase outlet then?

Yes (and it is a single phase outlet). The problem is that at 208V it will take more higher amperage to get the same amount of power.
Inspector 2211
Sr. Member

Offline

Activity: 453
Merit: 250

 March 30, 2012, 10:12:51 PM

Honestly, I wouldn't bother with an expensive PDU and an electrician and stuff.
That \$900 basically pays for an entire low-end (4 x HD 5830) rig.

Why don't you wire some kind of adapter cable that routes one 110V circuit to a \$5 power strip A and the other 110V circuit to a \$5 power strip B. Then, you start by plugging in two rigs to power strip A and two rigs to power strip B. This will definitely work. So far, so good.

The elephant in the room is what your circuit breakers actually are.
20A each?  This is what I had in Palo Alto, and I maxed them out.
35A each? 30A each? 40A each?
Check the circuit breaker panel. The circuit breakers should be labeled with the office suite #.

If you cannot clearly identify the circuit breakers, buy a \$29.99, 1000 W electrical space heater at Walmart.
Plug it into power strip A, while all miners are mining, and turn it on.
Then repeat for power strip B.
If the circuit breaker doesn't fall, you're good to go for another 2 rigs (one goes into strip A and one goes into strip B).
Now you got 6 rigs.

Rinse and repeat this simple test to get to 8 rigs.

I'd stop at 8 rigs, 4 on each side, for a symmetrical load.

Edit: In case a \$5 power strip is only rated for 10 A, you'd want more than one for each of the 110 V circuits. But the principle remains: No need to spend \$900 on this.

 ▄█▄            ▄█ ▀█▀     ▄ ▄███▄▄████▄▀ ▄▄▀▄    ▀█▄██████████▀▄█████▀▄▀   ▄█▀▄███████████████████▄ ▄██▀█▀▀▀▀███▀▀▀█████▄▄▄▀█▀▄ ▄█▀▀   ▀████▀▄████████ █▀█▄▄██▀  ▀ ▀ ▀██████████▄   ▄▀▀█▄     ▀ ▀  ███▀▀▀▀▀████▌ ▄  ▀          ████████████▌   █        █████████████▀        ▀▀▀██▀▀██▀▀           ▀▀  ▀▀ BTC-GREEN ▄▄█████████▄▄    ▄█████████████████▄  ▄█████████████████████▄ ▄███████████████████████▄▄█████████████████████████▄█████████████████████████████████████████████████████████████████████████████████▀█████████████████████████▀ ▀███████████████████████▀  ▀█████████████████████▀    ▀█████████████████▀       ▀▀█████████▀▀ Ecological Community in the Green Planet❱❱❱❱❱❱     WHITEPAGE   |   ANN THREAD     ❰❰❰❰❰❰ ▄███▄▄       ▄▄█████████▄      ▄█████████████▌   ▄████████████████▄▄ ▄███████████████████████████████████████████▄▄███████████████████████▀████████████████████████▀ ▀▀███████▀██▌████████▀   ▀██▀▀▀  ██  ▀▀▀▀▀▀           ██           ██▌          ▐███▄ .J O I N   I C O  IIILIVE
 Pages: 1 [2]  All
 « previous topic next topic »